ORGANIZATIONAL TROUBLESHOOTING - CONTINUED
TEST OR INSPECTION
Set multimeter to 20 vdc scale. Connect red test lead to wire terminal (7) on wire connector (8) and black
test lead to ground. Check for 11 to 13 vdc on multimeter. Disconnect test leads.
If multimeter does not read 11 to 13 vdc, 55B wire (9) must be replaced. Notify Direct Support Maintenance.
If multimeter reads 11 to 13 vdc, install instrument panel pad (page 2-424). Go to step 8.