ORGANIZATIONAL TROUBLESHOOTING - CONTINUED
TEST OR INSPECTION
Step 4.Set multimeter to 20 vdc scale. Connect red test lead to socket end (9) and black test lead
to ground. Rotate DOME/PNL light switch (7) until click is felt. Check for 11 to 13 vdc on
multimeter. Rotate DOME/PNL light switch (7) to dim position. Disconnect test leads.
If multimeter does not read 11 to 13 vdc, lamp (10) must
be replaced (page 2-719).
If multimeter reads 11 to 13 vdc, go to step 5.